Indirect water heater, stationary 0.6 MPa – embedded heating element into flange 2,2 kW. The heater with 1m2 tube exchanger and dry ceramic unit. 885 x 524 mm
Warning: Last items in stock!
Capacity: 96 l
Weight: 59 kg
Operating pressure in the tank: 0,6 MPa
Operating overpressure in the exchanger: 1 MPa
Max rating water temperature: 110 °C
Max temperature of HSW: 80 °C
Lower exchanger heat delivery surface: 1 m2
Bottom exchanger output at rating water temperature of 80 °C and flow 720 l/h: 24 kW
Permanent output HSW: 610 l/h
Time of heating by exchanger from 10 °C to 60 °C: 14 min
Time of rating with electricity from 10 °C to 60 °C: 3 h
Power input: 2,2 kW
Electric connection of control elements: 1 PE-N 230 V/50 Hz
IP protection: IP 44
Standing loss: 42 W
The water heater Dražice OKCE 100 NTR / 2,2 kW are suitable for installation with various energy sources (e.g. condenser gas boiler, solid fuel boiler). The models usually include the exchanger surface, they can transfer higher boiler output and the heating period becomes shorter. It can be connected to electricity network.
Thanks to their construction and number of variants, the OKCE 100 (125 NTR) series storage tanks enable economic preparation of hot service water (HSW) by means of various power sources. Their nominal performance provides sufficient amount of hot water for flat units, premises, restaurants, and similar establishments. For HSW reheat, electricity, various types of central heating boilers, recoverable energy sources (heat pumps, solar collectors) and combination of those can be chosen.
Service water heating via thermal energy through heat exchanger
Closing valves of the heat exchanger must be opened which ensures heating water flow from the hot water heating system. Together with a closing valve, it is recommended to install an air outlet valve at the inlet to the heat exchanger in order to bleed the heat exchanger as needed, in particular before the beginning of the heating season. The time of heating using the heat exchanger depends on the temperature and flow of water in the hot water heating system.